Hi, Im Stephany and welcome to restore andReplace, your on-line resource for rapid and easy repairs. At present, had been going to perform a continuitytest for your fuel furnace ignitor. A scorching surface ignitor works in a similar way to anincandescent gentle bulb. As electricity flows via the aspect,the resistance within the fabric generates warmness. This flash of warmness motives the fuel to ignite.The ignitor can burn out over time with normaluse and may just appear singed or cracked. This can be complicated to peer, as even a smallbreak can intent an ignitor to fail. It is first-rate to participate in a continuity scan asthis will verify if a continuous electrical course is reward. Without continuity, the ignitor is not going to operate. All youll want is your hot surface igniterand a digital or analog multimeter. First, disconnect all vigour to your furnaceand isolate or get rid of the ignitor.Be careful when handling the igniters and dont contact the detail along with your fingers. If you happen to use an analog multimeter, set the multimeterto the bottom Ohms of resistance. Next, touch the probes together and adjustthe needle until it can be calibrated at "0". In case you are utilising a digital multimeter, alsoset the dial to the lowest Ohms of resistance. To scan for continuity, take a probe fromthe multimeter and touch it to one of the most terminals. Now, touch the 2nd probe to the remainingterminal. If the igniter has continuity, your multimetershould learn at any place from 30 to 200 Ohms. If there’s no reading on the multimeter orvery little alternate, then there’s no continuity and you’ll haveto change the igniter.In the event you located this video valuable, hit "like". To hold up to date on our repair and Replaceplease subscribe, and for the widest choice of constituents, lowprices and equal day delivery, discover our website beneath. Thanks for gazing..
Hi, I’m Vance and welcome back to Repair and Replace. I’ll show you how to replace the hotsurface igniter in a gas furnace. This is one of the most common points of failure and it can easily be tested before replacing. Hot surface igniter works similarly to an incandescent light bulb. As electricity flows to the element the resistance in the material generates heat, which causes the gas to ignite. Over time the igniter can burn out and may appear singed or cracked. Now this can be difficult to see as even a small break can cause the igniter to fail. If the inducer motor runs But the igniter doesn’t glow, then it’s best to test the igniter for continuity before replacing. To begin you’ll need a hot surface igniter, a screwdriver or nut driver and a multi-meter. Now there are a few different styles of igniters available each with a different shape and size.So visit our website to find the right replacement. Also, be aware that there are no returns orrefunds on electronic items once installed. So, you may want to consult a trainedprofessional before purchasing. When working on your furnace alwaysshut off the power and close the gas valve. Remove the top cover panel. Many furnaces use a push lock or twist lock, some furnaces will require a screwdriver or socket wrench. Trace the gas line up to the burner, the igniter should be on this side.In some furnaces it’ll be hidden behind a cover. Now disconnect the wires. Next unscrew and remove the igniter,but be careful not to touch the element. Take the multi-meter and set it to the lowest Ohms of resistance. Now touch the probes to each terminal. if the igniter has continuity your multi-meter should read anywhere from 30 to 200 Ohms. If there is no reading on the multi-meter or just a slight change, then there is no continuity, and you will have to replace the igniter Align the new igniter and tighten the screw. Now reconnect the wires. Now replace the upper cover. Next open the gas valve, Now turn on the power to your furnace. The furnace should be running normally. If you’re still unsure what’s causing the problem in your furnace, Then watch our troubleshooting guide for a step-by-step breakdown, and there’s a link to this in the description below. If you found this video useful then Subscribe to our Channel. We’re constantly filming new content every week, so let us know what repairs you’d like to see next.And if you need a part for that repair then visit our website. We stock thousands of hard-to-find parts,and we’ll ship it out to you the same day. Thanks for watching!.
Hi, i’m Vance and welcome back to restore and replace. Furnace is whatever you certainly not particularly feel about unless it stops working, however with a little bit little bit of advantage,it is a lot less difficult to troubleshoot problems. So at present we ‘re gonna study how a gas furnace works. First we will cover the fundamentals, then we’ll dive somewhat deeper into the sequence of operation. So which you can fully grasp what every component does. Let’s begin ! Although there are some variations, all gasoline furnaces work in the equal common means. Ordinary gasoline is burned to heat up the heat exchanger. The exhaust fumes are launched via the flue gasoline vent. The blower fan then pushes air over the warmth exchanger and circulates it around your residence. The furnace runs until the thermostat detects the correct temperature and shuts the furnace off. Brand new furnaces use a draft inducer fan to aid exhaust the emissions, this drive draft also increases the efficiency.Condenser furnaces use a twin warmth exchanger to condense water vapor , this extracts much more heat out of the combustion. Furnaces are rated with the aid of AFUE or (Annual fuel Utilization effectivity). This quantity is a ratio of the fuel burned versus the gas changed into heat. Older furnaces will have an efficiency score of 70 AFEU or much less, which means that handiest 70 percent of the gas is was usable warmth. Mid efficiency furnaces are around eighty and high-effectivity condenser furnaces are frequently ninety and above. Furnaces can also be single stage or dual stage. Single stage furnaces run at one velocity, which means it can be both full warmth, or no warmth. Two stage furnaces can run at full velocity or a diminished velocity when less warmth is needed.This permits for the furnace to run quieter and may contain a more constant temperature. Modern furnaces have a collection of protection switches that shut down the furnace, when the system is compromised. If a switch is tripped, it will rationale the furnace to lockout. The furnace will strive ignition, a number of occasions earlier than going right into a difficult lockout for as much as an hour. Whenever a lockout happens the furnace will use flashing lights, as codes to determine the supply of the shutdown These codes are precise to every mannequin so check your furnace manual to look what each code method. When the thermostat calls for warmness, voltage is distributed to the manipulate board. Next the draft inducer fan pulls contemporary air into the burner, which makes it possible for for clean and effective combustion. When the draft motor reaches full pace the stress switch will shut, enabling for the sequence to proceed. The pressure change ensures that there’s ample airflow inside the warmness exchanger to securely operate the furnace.If the stress is low, the change will keep open and will avert the furnace from igniting. If the stress is good, then voltage is sent to the hot surface igniter. Some furnaces might use a spark igniter alternatively. After the igniter heats up the fuel valve opens and the burners ignite. When the flame will continue so long as the security switches remained closed.If the flame is not detected after 7 seconds the flame sensor will shut off the gas. When the burner is lit, the blower fan is simply too late from going for walks to permit the heat exchanger to heat up. This prevents the furnace from circulating cold air. The blower fan then pushes the air over the warmness exchanger and circulates it around your home. The limit switch displays the temperature of the air passing over the heat exchanger and will shut off the furnace if the process overheats.Any restriction of the airflow might reason the warmth exchanger to overheat. That is why it is major to interchange the furnace filter every three to six months. As soon as the thermostat alerts that the temperature of the residence is normalized, the fuel is shut off and combustion stops. The blower motor will continue to run for a number of minutes until the furnace is cooled down. Eventually the unit is positioned in standby except the thermostat requires warmth once more. Hopefully, this has given you a better working out of how a furnace works. Now if your furnace is having hindrance running, then watch our troubleshooting guide for a step-via-step breakdown and there’s a hyperlink to this in the description under. If you observed this video priceless then subscribe to our Channel.We’re always filming new content material per week, so let us know what repairs you’d like to see subsequent and if you would like an element for that repair then discuss with our website. We stock thousands of tough-to-in finding elements, and we’ll ship it out to you the same day. Thanks for gazing.